What Is a Load Bank?
Testing power sources, such as uninterruptable power sources (UPS) and diesel generators, ensure that these devices will provide the required amount of power when needed. A load bank tests these power sources by developing an electrical load. Various load configurations permit testing under different conditions.
A load bank is a self-contained device that has the load elements, controls and cooling systems it needs to operate built-in. Power is delivered to a load bank, which then consumes the electrical power by applying it to a power source and either converting or dissipating the source's power output. Load banks use the energy produced to protect, support or test a power source while a "real" load or actual building load uses energy output productively.
What Is the Purpose of a Load Bank?
Load banks ensure the quality and reliability of your emergency power sources. They verify the accuracy of the generators' output capacities by creating a variety of different loads that replicate real-world use.
If you own, sell or operate generators, especially for backup power, you need to test them regularly. Without testing, you cannot be assured the generator will provide the required power when the lights go out. Many facilities require load tests of all backup power sources. Prime power generators benefit from load bank use, particularly in lightly loaded situations.
What Does a Load Bank Do?
A load bank develops an electrical load. Load banks are absolutely essential for emergency sources of power, as they verify the power source's rated output capabilities before the power source is called into actual use. A load bank should mimic the real load a power source would see during an actual use scenario. The devices usually have different levels of load, which allows critical systems to be tested under a variety of conditions.
Who Uses Load Banks?
You need this type of testing bank if you have generators or uninterruptable power sources in your business. Best practices for testing emergency power sources is regular load bank tests.
If you have diesel generators on-site, you may use a load bank to augment lightly loaded situations and keep your generator running properly. Wet stacking occurs when unburned fuel remains inside the system. The unburned diesel condenses and combines with soot in the exhaust system, leading to wet deposits on exhaust components. Left unchecked, wet stacking reduces engine efficiency until it requires a complete overhaul to restore its former power.